RADIK VKM - Steel Panel Radiator
The conception of RADIK VKM radiators is based on the VENTIL KOMPAKT design. The original design of the inner distribution allows the bottom middle connection of the radiator to the heating system. Two upper and two lower hangers are welded at the back of the radiator, radiators with length of 1800 mm and longer have six welded hangers.
RADIK VKM panel radiators are designed for use in modern pressurized heating systems with horizontally led distribution pipelines either under the radiator in the floor or in the wall.
The design of the RADIK VKM radiator is patent-protected.
|Height H||300, 400, 500, 600, 900 mm|
|Length L||400, 500, 600, 700, 800, 900, 1000, 1100, 1200,
1400, 1600, 1800, 2000, 2300, 2600, 3000 mm
|- Type 10 VKM||47 mm|
|- Type 11 VKM||63 mm|
|- Type 21 VKM||66 mm|
|- Type 22 VKM||100 mm|
|- Type 33 VKM||155 mm|
|Connecting pitch||50 mm|
|Connecting thread||6 x G½ inside|
|Maximum working pressure||10 bar|
|Maximum working temperature||110 °C|
|Radiator connection||Middle bottom|
Types of Connection
φ = 1
Overview of Types
|Type 10 VKM|
|Type 11 VKM|
|Type 21 VKM|
|Type 22 VKM|
|Type 33 VKM|
In case of two-pipe heating system it is necessary to calculate the correct level of valve presetting and specify this in the project documentation to ensure a proper function of the heating system. This must be kept by the installer during installation of the heating system.
In case of one-pipe heating system it is necessary to set the valve at level 6. For adjusting the required mass flow in the radiator we recommend to use the compact connecting fitting with a fixed or adjustable flow volume of water in the radiator.