RADIK HYGIENE VK
Steel panel radiator for rooms with high demands on hygiene and cleanness, with flat front panel and right bottom connection
RADIK HYGIENE VK is a panel radiator in VENTIL KOMPAKT version which enables right bottom connection to the pressurized heating system.
It is suitable for installation and operation in rooms with high demands on hygiene and cleanness. All types are without convector fins; they have a flat front panel and the seam welds are covered with a special flat strip. The type 20S has got a bigger spacing between the panels (radiator depth B = 102 mm) as compared to the standard spacing of type 20 (B = 66 mm).
There are two upper and two lower hangers welded at the back side of the radiator. Radiators in length 1 800 mm and more have six hangers. An air-vent and blanking plugs are delivered as standard. We recommend using the drill-in brackets (type 18/120 – see the KORAMONT catalogue) which enable to mount the radiator in a distance of up to 65 mm from the wall.
Notice: If the requested distance between the radiator and the wall should be 65 ÷ 80 mm, the same type of brackets can be used on condition that the lower hangers are fixed with brackets (not with supporting pieces only). In such a case the additional brackets must be ordered extra.
|Height (H)||503, 603, 703 mm|
|Length (L)||404, 504, 604, 704, 804, 904, 1004, 1104, 1204, 1404, 1604, 1804, 2004 mm|
|- Type 10 HYGIENE VK||49 mm|
|- Type 20S HYGIENE VK||102 mm|
|- Type 30 HYGIENE VK||157 mm|
|Connecting pitch||50 mm|
|Connecting thread||6 × G½ inside|
|Highest allowed working pressure||10 bar|
|Highest allowed working temperature (°C)||110 °C|
|Radiator connection||right bottom|
In case of two-pipe heating system it is necessary to calculate the correct level of valve presetting and specify this in the project documentation to ensure a proper function of the heating system. This must be kept by the installer during installation of the heating system.
Heat output [W]
- t1 - input water temperature
- t2 - output water temperature
- ti - desired room temperature
For the conversion of heat outputs change the default values.
Heat output calculated to ∆T= 50; (t1/t2/ti = for 75/65/20 °C)
|Type 10 HYGIENE VK||Type 20S HYGIENE VK||Type 30 HYGIENE VK|
|Height [mm]||Height [mm]||Height [mm]|
Mounting and accessories
Higher heat outputs and smarter design of KORALINE bench convectors
Local ventilation unit KORASMART TUBE with heat recovery
A new model of vertical panel radiator RADIK PREMIUM which thanks to its design and dimensions enables installation even in atypical spaces